ABB800M to Phoenix Contact Visu+ SCADA communication
Is there a way we can change the Com setting of ABB800M com protocol to be compatible with the Phoenix Contact Visu+?
In addition to the previous answer, with just a few steps this is possible:
1. Install the ABB OPC server on the SCADA system
2. Connect to the controller
3. The OPC server needs some files, you can find them in your Control Builder project folder.
4. Connect the Phoenix Contact Visu+ Scada OPC client to the ABB server.