Advant MOD300 communication problems
We have AC460 controllers with CS512 communication interface module and AdvaBuild 3.7 Station with the PU412K01.
Unfortunately i don't have original TC530K01 cable and use straight-thru pinout. Is it right? Can anybody show me wiring diagram for this cable?
I connect computer in PC1 port on PU412 and CS512 in DCN1 port. I see PU412 in RNRPMon.
All proceses in PAS is in a Started state, but i don't see Active state in System Status for at least one controllers.
I think that, when PU412 connected to PC, DCN indicators in System Status Client for this Station must be green, isn't it?
What must i do to make communication whis this controller, please help me.
Thank in advance
Voted best answer
you must use 2 T-box TC530 with DCN cables.
One T-Box connected on your adavbuild (via PU412) and another T-box connected with another node (whatever node).
You must create a loop with the DCN (In to Out and In to Out).
I give you the drawing of the cabling (DCN.pdf file) but it's an old drawing and you don't put the C connection because it's linking with the shield of the cable.
Connect only the A and B connection on the DCN cable.
Normally, you shauld have the green status of 2 nodes.
Let me know if you have problems.